Project CategoryMain project classification
During the design and implementation of the clean room project, there are many issues that need attention. If you don't pay attention, it will cause adverse effects and irreparable consequences. It may take a huge amount of material resources, and the financially constructed projects do not achieve the desired results, affecting the quality of the clean room and the progress of the project. So, some notes about the clean room engineering are as follows:
1. Pay attention to energy-saving work in air-conditioning purification. The air-conditioning itself consumes a lot of energy and has a large loss. During the installation and implementation, pay attention to the division of the system area, the calculation of the supply air volume, and the determination of the temperature and relative temperature. Determination of cleanliness level and number of air changes, fresh air ratio, air pipe insulation, the effect of bite form in air pipe production on air leakage rate, the influence of main pipe branch pipe connection angle on air flow resistance, whether the flange connection is leaking, etc. The selection of equipment such as fans, chillers and chiller units are all related to energy consumption. These related factors must be taken into consideration, repeated tests and inspections, and accurate records.
2. Air ducts require economy and efficiency. In centralized or purification air conditioning systems, the requirements for air ducts are both economical and effective for supplying air. The former requirements are reflected in cheap prices and convenient construction of dust-free workshops, and operating costs. The inner surface is smooth and has low resistance. The latter means good tightness, no air leakage, no dust generation, no dust accumulation, no pollution, fire resistance, corrosion resistance, humidity resistance, etc. During operation, sometimes the local resistance of the pipe is much higher than the resistance along the air pipe. This situation needs to be improved. The pipe mainly has elbows, reducers and tees. The center curvature radius of the bend should be Larger than the length of the side of the rectangular duct, the diameter of the round is doubled. For large cross-section ducts, deflectors should be added in the ducts to reduce the resistance. In actual installation and construction, this is rarely done. Reducing diameter, it should be made into a gradually expanding (shrinking) pipe. The expanding angle of each side of the gradually expanding pipe should be greater than 15 degrees. The shrinking angle of each side of the shrinking pipe should not be greater than 30 degrees. , The branch pipe should also have a certain radius of curvature, if you want to divert 90 degrees, you should add a baffle in the elbow.
3. The air-conditioning box should be selected according to the local climatic conditions. Regarding the selection of the air-conditioning box, the climate environment should be considered. For example, in northern areas where the winter temperature is low and the dust content in the air is large, a fresh air preheating section should be added to the general-purpose air-conditioning unit and water spray air treatment should be adopted. Method to make it not only wash the air and produce heat and temperature exchange to achieve the required temperature and humidity, but in the southern regions where the climate is humid and the air dust concentration is low, there is no need to preheat the fresh air in winter, Filtration and temperature and humidity adjustment use the initial effect of filtration, the surface cold surface temperature and humidity adjustment can also strengthen the temperature dehumidification process, and then through the intermediate efficiency filtration and terminal high-efficiency or sub-high-efficiency filtration, air-conditioning box supporting fan is best to use variable frequency fan This not only saves energy, but also allows flexible adjustment of air volume and pressure.
4. The automatic control device guarantees full adjustment. At present, many manufacturers use manual methods to adjust the air volume and air pressure. However, since the control valves that control air volume and air pressure are in the technical compartment, and the ceilings are also soft ceilings made of color steel, they are basically installed and adjusted. it is good. Since then, most of them have not been adjusted, nor can they be adjusted. In order to ensure the normal production and work of clean plants, a relatively complete set of automatic control devices should be set up to achieve the following functions: monitoring of clean room air temperature, humidity and pressure difference , Damper adjustment, temperature, pressure, flow detection, gas purity, pure water quality monitoring of high-purity gas, pure water and circulating cooling water, etc., the air filter of purification air-conditioning system increases resistance with the increase of operating time In order to maintain the air volume, the air valve in the system needs to be adjusted. When the system is started during system commissioning, in order to start the fan at no load, the air valve at the fan outlet needs to be closed. After the fan is started, the air valve is under great pressure. It is very difficult to turn on. After using the variable frequency speed control device of the fan to control the change of the pressure difference between the front and rear of the air filter, the adjustment of the supply air volume will become very easy and the supply air pressure will be stable. These monitoring devices can be adjusted to measure in a single system. The control system can also be adjusted to a distributed computer control and management system. When the air conditioning system is stopped and the wind is stopped or there is no overheating, the electric heater will continue Electric heating, resulting in equipment damage or even fire, in order to avoid this situation, should be set no wind and over-temperature shutdown protection.