What purification equipment should be installed in the clean room?
进风系统要安装，新风过滤箱，中央净化空调（中央净化空调要分为初效/中效/高效三个过滤段）末端有高效送风口。 First, the air inlet system of the dust-free purification workshop should be installed, the fresh air filter box, and the central purification air conditioner (the central purification air conditioner should be divided into three stages of primary efficiency / medium efficiency / high efficiency) have efficient air outlets. If necessary, a purification booster box is also installed.
回风系统要安装，回风口，过滤初效器，中效回风箱。 Second, the return air system of the dust-free purification workshop shall be installed, the return air port, the primary filter of the filter, and the intermediate return air box.
之前先进入缓冲区，缓冲区门安装电子互锁，更衣处放置洁净储衣柜，空气清新机。 Third, enter the buffer zone before entering the dust-free purification workshop . The buffer door is installed with electronic interlocking. A clean storage closet and air freshener are placed in the changing area.
Fourth, people and goods must pass through to enter the dust-free purification workshop, air shower room, cargo shower room, and transfer window mainly pass small items.
Fifth, vertical laminar flow benches, laminar flow hoods (FFUs), clean sheds (movable purification work sheds), and self-purifiers must be installed in places where the dust-free purification workshop needs to reach the level of 10-1000. Laser dust particle counter for measuring clean room cleanliness
不同级别空气洁净度的空气过滤器的选用、布置要点：对于300000级空气净化处理，可采用亚高效过滤器代替高效过滤器；空气洁净度100级、10000级及100000级的空气净化处理，应采用初、中、高效过滤器三级过滤器；中效或高效空气过滤器宜按小于或等于额定风量选用；中效空气过滤器宜集中设置在净化空气调节的正压段；高效或亚高效空气过滤器宜设置在净化空气调节系统的末端。 Selection and layout of air filters for different levels of air cleanliness in dust-free workshops : For 300,000 air purification treatment, sub-high efficiency filters can be used instead of high efficiency filters; air cleanliness of 100, 10,000 and 100,000 air purification For treatment, three levels of primary, intermediate and high-efficiency filters should be used; medium-efficiency or high-efficiency air filters should be selected based on less than or equal to the rated air volume; medium-efficiency air filters should be concentrated in the positive pressure section of purified air conditioning; high efficiency Or sub-high efficiency air filters should be installed at the end of the purified air conditioning system.
Related links: Dongguan air-conditioning purification project, Dongguan dust-free purification equipment, Changan central air-conditioning project, low-voltage power distribution project, Dongguan purification ventilation project, Dongguan dust-free purification project, hydropower installation project, Dongguan 100,000-level dust-free workshop, Dongguan City Power Xiang Air Conditioning Purification Engineering Co., Ltd.
Article source: http://jimesale.com Tan Yuming 13751461639