Project CategoryMain project classification
First, enter the clean area:
1) When the person entering the clean area opens the outer door, the electric lock of the inner door is automatically locked to prevent the unpurified air in the wind shower room from flowing into the clean area.
2) After entering the air shower room and closing the outer door, please stand in the induction zone. The system's infrared probe starts to detect if someone is there. If someone is detected, the system goes into the air shower process.
3) The internal and external doors are locked before the wind shower, the fan starts to start the wind shower, and at the same time, the wind shower countdown starts.
4) If the system cannot detect any person in the shower room within a specified time after the outer door is closed, return to the standby state.
5) During wind shower, when someone presses the up, down, and lighting switch.
6) After the wind shower is over, the inner door is unlocked and the voice prompt: "After the shower is complete, please exit from the back door".
7) After the person exits the air shower room and closes the inner door, the system returns to the initial state and waits for the next use.
8) After the wind shower is completed, the inner door is unlocked. The personnel inside did not leave the air shower room within the specified time, the system defaulted that the person may have left, and automatically returned to the standby state.
9) After the lighting lamp is lit, if it is not triggered again within a specified time, it will go out automatically.
2. Leaving the clean area:
1) Open the inner door, the electric lock of the outer door is self-locking, the lighting of the air shower room is on, and the work indicator is on;
2) When a person enters the air shower room and closes the inner door, the system starts to detect whether someone is in the air shower room. If no one is detected within the specified time, the inner and outer doors are unlocked;
3) If someone is detected, the system locks the inner door when the system opens the outer door. When the outer door is closed, the system returns to the initial state.
4) In special circumstances, the personnel can choose to return to the clean area. The system waits for the personnel to open the inner door, and the outer door is self-locked. When the inner door is closed, the system returns to the initial state;
5) After the outer door is opened, if no one is detected within the specified time, if the outer door is opened first at this time, the system will switch to the process of entering the clean area; if the inner door is opened first, the system will switch to the process of leaving the clean area.
6) After the lighting lamp is lit, if it is not triggered again within the set time, it will go out automatically.
无尘车间、东莞市力翔空调净化工程有限公 司 Related links: Dongguan air-conditioning purification project, Dongguan dust-free purification equipment, Changan central air-conditioning project, low-voltage power distribution project, Dongguan purification ventilation project, Dongguan dust-free purification project, hydropower installation project, Dongguan 100,000-level dust - free workshop, Dongguan City Power Xiang Air Conditioning Purification Engineering Co., Ltd.
Article source: http://jimesale.com Tan Yuming 13751461639